Created a BACnet digital output under the BACnet Interface in the Automation Server but the Out of service property indicates 'True' and get the error 'Property value out of range' when attempting to set the out of service to false.
EcoStruxure Building Operation
- Automation Server - AS
- BACnet Interface
BACnet output must be associated with an IO Bus output.
See Associate AS BACnet Interface IO points with points on the IO bus in SmartStruxure 1.4 and above for instructions on setting the associated value.