Can WorkPlace Tech Link Builder be used to link I/A BACnet controllers to third party BACnet devices?
WorkPlace Tech (all Version)
I/A controllers do not have the ability to write to third party BACnet devices.
Link builder will only link data from a third party device to BACnet "COVs" in our IA controllers.
Our I/A controllers can pull data into our controllers as a client, but they can not function as a server and push data to third party devices.