On a jobsite, an energy meter was converted from a pulse output to a voltage output. Can the analog input be totalized in the associated MNL controller like the pulse input was previously?
Analog values cannot be totalized in the MNL controller. The next best option is to send the real-time analog value to the area controller (i.e. Niagara UNC or ENC) via a nvo and use the features available at that level for totalization.