- SNVT_press_p cannot represent a value above 32766 Pa
- Sending a value of 15psi out of a Menta application using a SNVT_press_p and it is arriving at the receiving controller as 4.75psi.
All LON communication is transmitted in metric units, so the data sizes are limited by the valid range of Pascals (or kiloPascals for SNVT_press).
There are three different SNVT types defined to represent a pressure (gauge) value. SNVT_press, SNVT_press_f, and SNVT_press_p. It is important to recognize the valid ranges of data each one can represent.