The documentation states in different ways that the sensors are both 0-95% and 0-100% RH range.
Different RH (Relative Humidity) values are listed in the documentation, and needs to be explained.
Ranges are divided into "measuring range" and "working range".
Measuring range: 0…100% r.H.
Working range: 10…100% r.H. ( non condensing )
Normally 100% r.H. is already water but it is possible to have 100% r.H. in air- or gas form.
Sensor works at 100% r.H. in air but not if pure water is present.
This is why “non condensing” is added. In this case working range is 10…100%.
If we don’t add “non condensing”, specification should read: 10…95% r.H.
Sensor will not become damaged because of condensing.