There is an adapter which allows for connection between the USB port of a laptop or computer to Micronet via a MicroNet 2000 MN-Sx sensor.
MicroNet 2000 software (MN-CI, MN Flow Balance)
MicroNet 2000 controller with attached sensor (MN-S, MN-SO, MN-SDK)
Computer without a serial port
This connection requires the use of both part numbers MN-CIM (MicroNet Controller Interface Module) and UC232A (USB to Serial Adapter). The UC232A adapter can be attained from B&B Electronics.
(NOTE: MN-CIM is obsolete as of December, 2011. See Product Announcement PA-000164. There is no functional replacement available)
- Load the UC232A driver
- Select unused Com port in setup (can not conflict with any other ports being used)
- Reboot computer