All the doors under ACX5720 can not be loaded with an attribute. The system status value goes back to "Nodatabase" after reloading the ACX controller.
- Continuum 1.94
The channel configuration may not be correct.
- Set all the channel numbers to 0 for the door, select the door separately, and send it to the controller
- If there is no error when sending the door to the controller, then reset the all the channel numbers correctly.
- Change the value of systemstatus to "Normal", then reload the ACX controller
Similar was seen on another site. Some doors no longer opened on a card swipe. the event type was "Invalid attempt", the message event was "No Destination Area", when reloading the controller or just a door object the error below was seen in the distribution properties
"UNABLE TO RELOAD ATTRIBUTES FOR (**DOOR NAME**). UNABLE TO RELOAD OBJECT. ERROR TEXT UNDEFINED (TBD) 0X00002001. AN ERROR WAS DETECTED WHILE ATTEMPTING TO SET AN ATTRIBUTE IN A REMOTE INFINITY OBJECT"
In this case the channels needed to be changed offline to zero, then the whole controller reloaded. The correct channels could then be put back in online.